The place in check safety hazards and make people worry
Publish Time：2017/07/31Click Rate：
Cctv.com news (Law Online): it seems that do not pay attention to fire safety, once triggered a fire is really regret at the end and, although the fire department issued units should strictly abide by the provisions of the fire, but there are still many units of luck. Recently, the Chengdu fire inventory on a number of illegal sites, there are some local fire safety hazards the really surprising.
Some time ago, Chengdu "Meigaomei international entertainment club" because there are nine serious fire safety hazards were seized, the reporters follow the fire department to the scene to look into the scene. Meigaomei, the reporter found that the dance hall and Changle "Latin" bar, Shenzhen dance song and dance hall, in the ceiling, walls, carpet the use of a large number of easily combustible materials. Look at this exit, perhaps for reasons of beautiful decoration, fire doors removed, is also surrounded by a thick decorative material wrapped up, so that the fire front lost the original function.
Not only is the fire doors were removed, the exit doors behind or to escape. However, such a song and dance entertainment with hidden dangers, in the center of Chengdu's business for eight years. It is located in Chengdu city Jinniu District peak era games, two pre export are fitted with iron the fence, seriously do not meet safety requirements.This is reminiscent of the serious fire in 2002 Beijing lanjisu cyber bar, Internet cafes because windows installed fences led to the house staff unable to escape, eventually led to the death of 24 people, 13 people were injured in the disaster. In addition, the game hall of the sprinkler system is not in conformity with the provisions.
After investigation, firefighters found the game hall is actually in the absence of any fire procedures in the case of unauthorized business. In the random inspection of fire personnel subsequently in several public gathering places more or less some fire hazard. Is it KTV fire facilities, seems to be very complete, can fire free picked up a fire extinguisher, found insufficient pressure already failure, this can be next to the fire inspection registration form but every day people are written signature confirmation, fire channel fire safety equipment is complete. The export of this cafe is not identified, and locked the door, the front also put two computer desk again. Look at the safety of this recreational place, fire doors open for many years, there is no installation of door closer, in the event of fire, smoke will quickly spread to the safe passage, thereby affecting the escape.
problems found in this examination, the fire department has asked the relevant units to rectify immediately